Courses

# Test: Psychrometric Chart & Its Application to Air-Conditioning - 2

## 10 Questions MCQ Test Thermodynamics | Test: Psychrometric Chart & Its Application to Air-Conditioning - 2

Description
This mock test of Test: Psychrometric Chart & Its Application to Air-Conditioning - 2 for Mechanical Engineering helps you for every Mechanical Engineering entrance exam. This contains 10 Multiple Choice Questions for Mechanical Engineering Test: Psychrometric Chart & Its Application to Air-Conditioning - 2 (mcq) to study with solutions a complete question bank. The solved questions answers in this Test: Psychrometric Chart & Its Application to Air-Conditioning - 2 quiz give you a good mix of easy questions and tough questions. Mechanical Engineering students definitely take this Test: Psychrometric Chart & Its Application to Air-Conditioning - 2 exercise for a better result in the exam. You can find other Test: Psychrometric Chart & Its Application to Air-Conditioning - 2 extra questions, long questions & short questions for Mechanical Engineering on EduRev as well by searching above.
QUESTION: 1

Solution:

QUESTION: 2

### When atmospheric air is heated at constant pressure its 1. Humidity ratio does not change 2. Relative humidity increases 3. Dew point temperature does not change 4. Web bulb temperature increases Which one of the following is correc

Solution:

Humidity ratio does not change

QUESTION: 3

### The Sensible Heat Factor of a room is given by (SHL = Sensible Heat Load and LHL = Latent Heat Load)

Solution:

Sensible Heat Factor

QUESTION: 4

The Latent Heat Factor of a room is given by (SHL = Sensible Heat Load and LHL = Latent Heat Load)

Solution:

Latent Heat Factor

QUESTION: 5

The main process which takes place in a desert cooler is

Solution:

In desert dry bulb temperature is very high and relative humidity is very low hence cooling and dehumidification process is used.

QUESTION: 6

If during the sensible cooling B is the by-pass factor, then coil efficiency is given by

Solution:

For coil
η + B = 1; η = 1 - B

QUESTION: 7

The by-pass factor for a cooling coil

Solution:

By pass factor decreases with an increase in the velocity of air passing through it.

QUESTION: 8

The heat load from the occupants in air conditioning load calculation is a source of

Solution:

Sensible heat load is due to following:
1. The heat flowing into the building by conduction through exterior walls, floors, ceilings, doors and windows due to temperature difference
3. Heat gained by lightnings, machineries, cooking operations, industrial processes etc.
Latent heat load is due to following:
1. Heat gain due to moisture in the outside air entering by infiltration.
2. Heat gain due to condensation of moisture from occupants.
3. Heat gain due to condensation of moisture from any process such as cooking.

QUESTION: 9

For air-conditioning the operation theatre in a hospital the percentage of outside air supplied is

Solution:

In operation theaters no ventilated air is supply while 100% fresh air is supplied due to requirement of sufficient Oxygen.

QUESTION: 10

In an air-conditioning plant the refrigeration load on the coil is 100 TR. The mass and enthalpy of air leaving the coil are 420 kg/minute and 40 kJ/kg respectively. What will be the enthalpy of the air at the inlet to the coil under these conditions,

Solution: