Three generators rated 100 MVA, 11 kV have an impedance of 0.15pu each. If in the same plant, these generators are being replaced by a single equivalent generator, the effective impedance of equivalent generator will be
Applying Thevenin's theorm
If all the sequence voltages at the fault point in a power system are equal, then the fault is a
For a solid fault i.e, Z_{f} = 0, V_{a1} = V_{a2} = V_{a0} for LLG fault.
A threephase transformer having zerosequence impedance of Z_{0} has the zerosequence network as shown in the figure below. The connections of its windings are
Which one of the following relays has the capability of anticipating the possible major fault in a transformer?
Buchholz relay takes care of all incipient internal faults.
In a 220 kV system, the inductance and capacitance up to the circuit breaker location are 25 mH and 0.025 μF respectively. The value of resistor required to be connected across the breaker contacts which will give no transient oscillations, is
or no transient oscillation.
The operating characteristic of a distance relay in the RX plane is shown in the figure below, It represents operating characteristic of a
Two power plants interconnected by a tieline as shown in the below figure have loss formula coefficient B11 = 103 MW1. Power is being dispatched economically with plant '1' as 100 MW and plant ꞌ2' as 125 MW. The penalty factors for plants 1 and 2 are respectively
Since the load is at the bus of plant2, therefore, the line loss will not be affected by variation of P_{2} . Thus B_{12} = B_{21} = 0 and B_{22} = 0
For a 2plant system
∴ Penalty factor for plant1
∴ Penalty factor for plant2
Penalty factor is given by
Where ITL means incremental transmission loss.
The below diagram shows the layout of a power station having two generators A and B, connected to the 11 kV buses which are also fed through two transformers C and D from a 132 kV grid. The 11 kV buses are interconnected through a reactor R.
The reactance of A, B, C, D and R in p.u. on a common MVA and kVbase. All the generated voltages in A, B and grid are each 1.0 p.u. and assumed as in phase at the time of fault.
The steady state symmetrical faultcurrent for a 3phase fault on the 11 kV feeders is
The speed regulation parameter R of a control area is 0.025 Hz/MW and load frequency constant D is 2 MW/Hz, The area frequency response characteristic (AFRC) is
∴
Where, Δf → change in frequency and ΔP_{D} → change in load demand.
The perunit impedance of a circuit element of 0.15. If the base kV and base MVA are halved, then the new value of the perunit impedance of the circuit element will be
The perunit impedance of an alternator corresponding to base values 13.2 kV and 30 MVA is 0.2 p.u. The p.u. value of the impedance for base values 13.8kV and 50 MVA in p.u. will be
For a given base voltage and base voltamp, the per unit impedance value of an element is X. What will be the perunit impedance value of this element when the voltage andvoltamp bases are both doubled?
The reflection coefficient for the transmission line shown in figure below at point P is
The line is terminated into its surge impedance so it is an infinite line.
A 3phase transmission line has its conductors at the corners of an equilateral triangle with side 3 m. The diameter of each conductor is 1.63 cm. The inductance of the line per phase per km is
A cable has inductance of 0.22 mH per km and capacitance of 0.202 μF per km. The surge impedance of the cable is
Z_{0} =
For some given transmission line the expression for voltage regulation is given by
In case of a short line, when load is removed, the voltage at the receiving end is equal to the voltage at the sending end. At full load V_{R}, _{Fl} = V_{R} and at no load, V_{R}, _{nl} = V_{S}
In a certain singlephase a.c. circuit the instantaneous voltage is given by v = V sin (ωt + 30°) p.u. and the instantaneous current is given by i = I sin (ωt  30°) p.u. Hence the per unit value of reactive power is
A surge of l00 kV travels along an overhead line towards its junction with a cable. The surge impedance for the overhead line and cable are 400 ohms and 50 ohms respectively. The magnitude of the surge transmitted through the cable is
A surge voltage rising at 100 kV/μs travels along a lossless opencircuited transmission line. It takes 10 μs to reach the open end. The reflected wave from the open end, will be rising at
V_{R} = V_{i} = 100 × 10 = 1000V/µs
As Z_{2} = ∞
At slack bus, which one of the following combinations of variables is not specified?
Load bus: Known quantities  P and Q Unknown quantities  V and δ
Generator bus: Known quantities  P and V Unknown quantities  Q and δ
Slack or reference bus: Known quantities  V and δ Unknown quantities  P and Q
Use Code STAYHOME200 and get INR 200 additional OFF

Use Coupon Code 







