The document Heat Exchangers - 1 Chemical Engineering Notes | EduRev is a part of the Chemical Engineering Course Heat Transfer.

All you need of Chemical Engineering at this link: Chemical Engineering

**The Exchanger**

The Design Equation for a Heat Exchanger

**Problem : Find the Required Length of a Heat Exchanger with Specified Flows: Turbulent Flow in Both Streams **

The design constraints are given in the schematic above. We show this as a countercurrent configuration, but we will examine the cocurrent case as well. The benzene flow is specified as a mass flow rate (in pound mass units), and the water flow is given as a linear velocity. Heat transfer coefficients are not provided; we will have to calculate them based on our earlier discussions and the correlations presented in earlier lectures. The inside tube is specified as "Schedule 40––1-14 inch steel."

Pipe "schedules" are simply agreed-upon standards for pipe construction that specify the wall thickness of the pipe. Perry’s Handbook specifies the following dimensions for

**the inside pipe :**

Schedule 40 1 1/4” pipe

D_{o} = 1.66 in. = 0.138 ft.

S_{c }= πD^{2} /4 = 0.0104 ft^{2 } (cross-sectional area for flow)

D_{i} = 1.38 in = 0.115 ft.

**the outside pipe : **

Schedule 40 2” pipe

D_{i} = 2.07 in = 0.115 ft.

To calculate the heat exchanger area, we must find A_{o} = πDL. We know the diameter; what is the length ?

The Design Equation is

The overall heat transfer coefficient, U_{o} , is given by

We can write it as:

To evaluate the parameters of the problem, we need the physical and thermal properties and conditions for flow in the system

T_{b} = 140˚F, ρ_{b }= 52.3 lbm/ft^{3} , C_{p} = 0.45 BTU/lb-°F

k_{b} = 0.085 Btu / h · ft ·°F

μ_{b} = 0.39 Cp_{ }

**Internal Film Resistance**

The Nusselt number on the inside of the inner pipe is given by the DittusBoelter equation

so that the film heat transfer coefficient

h_{i} = 249 Btu/h·ft^{2}·˚F

The heat transfer area per unit length is

so that the inner film resistance is

The other tube dimensions are

D_{oi} = 0.138 ft and D_{io} = 0.172 ft

**Calculation of the Water Flow Rate **

The hydraulic diameter is

Given the water velocity of 5 ft/s, we can solve for the water flow rate

W_{water} = 9300 lb_{m}/h

The Overall Energy balance

(wCp ΔT)_{benz} = (wCp ΔT)_{water}

Solving for the outlet water temperature:

7500 (0.45) (100 – 180) = 9300 (1) (70 – Tout)

gives the exit temperature as: Tout = 99˚F

**External Film Resistance **

The physical properties of the water must be estimated in order to determine the film heat transfer coefficient in the annular shell. The average water temperature T_{b} is calculated as 84.7 °F

μ = 0.8 cp, k = 0.34 BTU/h-ft-°F , ρ = 62.4 lb/ft^{3}

so that the Reynolds number can be calculated.

From the Dittus-Boelter equation, the Nusselt number is given as:

Nu = 0.023 Re^{0.8}Pr^{0.4} = 127

so that the external film coefficient, ho , is

h_{o} = 1270 Btu/h·ft^{2}·˚F

The external area/length is

so that the external film resistance is

**Conduction Resistance**

The last term in the equation for the overall heat transfer coefficient is

**Overall Heat Transfer Coefficient**

The overall resistance is

**Log-Mean ΔT**

Heat Load Q_{h} = wCp**ΔT** = 7500 (0.45) (180 - 100) = 2.7 x 105 Btu/h

Heating Rate/unit Length

Given the heat load, we can calculate the length of tubing so that

The case we considered was countercurrent flow, but we noted in an earlier example that in co-current flow we could be more fluid. Now is the pipe longer or shorter ?

**A Co-current Flow Heat Exchanger**

The Design Equation for a Heat Exchanger

The heat loads are identical, the Overall Resistances to heat transfer (UA)^{-1} are no different since the film coefficients do not change, but the ΔT_{lm} are different.

**Counter current**

T_{1 }(water) = 99

T_{1} (benzene) = 180

T_{2 }(water) = 70

T_{2} (benzene) = 100

ΔT_{1 }= 81

ΔT_{2} = 30

ΔT_{lm }= 51

L = 74

**Co-current**

T_{1 }(water) = 70

T_{1} (benzene) = 180

T_{2 }(water) = 99

T_{2} (benzene) = 100

ΔT_{1 }= 110

ΔT_{2} = 1

ΔT_{lm }= 23.2

L = 163 ft

There are two observations to be made. First that the tube length required for co-current flow is more than twice as long. Secondly that the approach temperature for co-current flow becomes diminishingly small.

Offer running on EduRev: __Apply code STAYHOME200__ to get INR 200 off on our premium plan EduRev Infinity!

59 videos|70 docs|85 tests