Heat Transfer in Boiling & Condensation - 4

# Heat Transfer in Boiling & Condensation - 4 Notes | Study Heat Transfer - Mechanical Engineering

## Document Description: Heat Transfer in Boiling & Condensation - 4 for Mechanical Engineering 2022 is part of Boiling & Condensation for Heat Transfer preparation. The notes and questions for Heat Transfer in Boiling & Condensation - 4 have been prepared according to the Mechanical Engineering exam syllabus. Information about Heat Transfer in Boiling & Condensation - 4 covers topics like and Heat Transfer in Boiling & Condensation - 4 Example, for Mechanical Engineering 2022 Exam. Find important definitions, questions, notes, meanings, examples, exercises and tests below for Heat Transfer in Boiling & Condensation - 4.

Introduction of Heat Transfer in Boiling & Condensation - 4 in English is available as part of our Heat Transfer for Mechanical Engineering & Heat Transfer in Boiling & Condensation - 4 in Hindi for Heat Transfer course. Download more important topics related with Boiling & Condensation, notes, lectures and mock test series for Mechanical Engineering Exam by signing up for free. Mechanical Engineering: Heat Transfer in Boiling & Condensation - 4 Notes | Study Heat Transfer - Mechanical Engineering
 1 Crore+ students have signed up on EduRev. Have you?

Illustration 6.1

Saturated steam at 70.14 kPa is condensing on a vertical tube 0.5 m long having an outer diameter of 2.5 cm and a surface temperature of 80oC. Calculate the average heat-transfer coefficient.

Solution 6.1

It is a problem of condensation on a vertical plate, thus eq.6.10b can be used,

where, different liquid and steam properties are evaluate at average film temperature,

Using steam table, the temperature of the steam corresponding to 70.14kPa pressure is 90oC. The average film temperature will then be the average of 80 oC and 90 oC and it comes out to be 85 oC,

Using given data the different properties can be found using steam table and other relevant tables given in the standard literature. The data is tabulates below at 85oC,

On putting the above values in the above equation,

hav = 1205.2 W/m2 °C

6.5 Condensation for horizontal tube

6.5.1 Condensation outside horizontal tube or bank of tube
This type of condensation is very common especially for the shell and tube heat exchanger. In case of condensation outside the vertical array of horizontal tubes the condensate flows as a film along the cylindrical surface or it may drop down. In case of another tube below, the condensate film flows down from the bottom edge of the upper tube to the upper edge of the bottom tube. As it goes on to the lower tubes, the thickness of the condensate film increases. Some of the correlations are given below.

6.5.1.1 Condensation on a single horizontal tube

(6.13)

6.5.1.2 Condensation on a vertical tube of N horizontal tubes

(6.14)

6.5.1.3 Condensation inside a horizontal tube
Figure 6.5 shows the physical picture of the condensation inside a horizontal tube (like an open channel flow).

Fig. 6.5: Film condensation inside a horizontal tube

Case 1: The length is small or the rate of condensation is low.

This situation will have small thickness of the flowing condensate layer at the bottom of the tube and the following coefficient can be used,

(6.15)

where,  and the vapour Reynolds number (Rev) should be less than 35,000. The Rev is calculated based on inlet condition of vapour and inside diameter of tube.

Case 2: The length is high or the rate of condensation is high.

In this the following relation can be used.

(6.16)

where,

(Condition: Rel >5000, Rev > 20,000)

where, Gl and Gv are the liquid and vapour mass velocities calculated on the basis of the cross-section  of the tube.

6.6 Correlations for packed and fluidized bed

6.6.1 Packed bed
The heat transfer correlation for gas flow through a packed bed is given as,

(6.17)

Conditions to use eq.6.12 are,

where,

is the Stanton number.

is the particle Reynolds number

dp = Diameter or the effective diameter of a particle

v0 = Superficial fluid velocity. It is the velocity based on the cross-section of the bed).

∈ : Bed porosity or void fraction

∈ : 0.3 → 0.5

Theoretically :   ∈ = 0.69 for uniform shape

= 0.71 bed of cubes

= 0.79 bed of cylinder

Colburn factor

6.6.2 Fluidized bed

The heat transfer coefficient to or from particles in a fluidized bed can be estimated with the help of following correlation,

(6.18 )

where, v0 is the superficial velocity.

The document Heat Transfer in Boiling & Condensation - 4 Notes | Study Heat Transfer - Mechanical Engineering is a part of the Mechanical Engineering Course Heat Transfer.
All you need of Mechanical Engineering at this link: Mechanical Engineering

## Heat Transfer

58 videos|70 docs|85 tests
 Use Code STAYHOME200 and get INR 200 additional OFF

## Heat Transfer

58 videos|70 docs|85 tests

### Top Courses for Mechanical Engineering

Track your progress, build streaks, highlight & save important lessons and more!

,

,

,

,

,

,

,

,

,

,

,

,

,

,

,

,

,

,

,

,

,

;